(RU2140545-C1)      The power plant includes one or more integrated unit modules (55a-c) each having a steam turbine (60a-c) responsive to the steam and producing power and heat depleted steam. A steam condenser (62a-c) associated with the steam turbine operated at a pressure not less than atmospheric pressure for condensing the heat depleted steam and vapourizing organic fluid, preferably pentane, applied to the condenser. A closed organic rankine cycle turbine (70a-c) operates on the organic working fluid for producing power. A device supplies the steam to the steam turbine in parallel to the steam turbines (60a-c) in the modules (55a-c).    A control valve (57a-c) is associated with each module (55a-c) and positioned before the steam turbine (60a-c) contained in the module for controlling gthe amount of steam supplied to the steam turbine via the steam supply device. A device (59) compresses non-condensable gases collected in the steam condenser(s) (62a-c) and vents the compressed non-condensable gases into a reinjection well.    ADVANTAGE -   Since source steam is distributed to various modules at pressure of steam source, diameter of distribution piping and size of control valves are small, thus, reducing cost.    (JP3166033-B2)      The power plant includes one or more integrated unit modules (55a-c) each having a steam turbine (60a-c) responsive to the steam and producing power and heat depleted steam. A steam condenser (62a-c) associated with the steam turbine operated at a pressure not less than atmospheric pressure for condensing the heat depleted steam and vapourizing organic fluid, preferably pentane, applied to the condenser. A closed organic rankine cycle turbine (70a-c) operates on the organic working fluid for producing power. A device supplies the steam to the steam turbine in parallel to the steam turbines (60a-c) in the modules (55a-c).    A control valve (57a-c) is associated with each module (55a-c) and positioned before the steam turbine (60a-c) contained in the module for controlling gthe amount of steam supplied to the steam turbine via the steam supply device. A device (59) compresses non-condensable gases collected in the steam condenser(s) (62a-c) and vents the compressed non-condensable gases into a reinjection well.    ADVANTAGE -   Since source steam is distributed to various modules at pressure of steam source, diameter of distribution piping and size of control valves are small, thus, reducing cost.